Hep2O Programmable Room Thermostat by Wavin (Formally coded 52uh973) 15UH373
£54.49 Inc VAT
£45.41 Exc VAT
£71.06 RRP 23% Saving
Available for Next Day Delivery
if order placed before 3:00pm
Please note formally coded 52uh973 new code ref 15uh373
Wavin Hep2O Manufacturer's part number: 52UH973.
Hep2O Wired Programmable Room Thermostat - 24V Bus programmable digital room thermostat for use with the Hep2O 14-zone Control Centre , designed for control of a single or multi-zone Hep2O UFH systems, both in new build and renovation projects.
Hep2O Programmable Room Thermostat lets you choose what times you want the heating to be on, and what temperature it should reach while it is on, allowing you to select different temperatures in your home at different times of the day (and days of the week) to meet your particular needs.
Hep2O Programmable Room Thermostat by Wavin features and benefits:
Hard-wired to the Control Centre.
Convenient and comfortable temperature control.
7-Day programmable - every day can be programmed separately to ensure optimum energy usage.
‘Optimised Start' feature - when activated, the Thermostat will adjust the start time to achieve the desired temperature at the start of the programmed time.
Party Mode - boosts the temperature by 2oC above the comfort setting until the next programmed change.
Frost Alarm - integral frost protection set at 3oC (installer adjustable between -10oC and + 10oC).
Fire Alarm - default setting at 60ºC (adjustable by installer between +50ºC and +70ºC), electronic signal, not audible without connection to an alarm circuit.
Easy to configure.
Easy to operate via a ‘jog' dial.
Use the domestic electricity supply instead of batteries.
Ideal for future-proofing the installation for different thermostats.
All wired thermostats are wired into 2 central terminals in the Hep2O Control Centre at first fix stage, then synchronised with the relevant circuit later, eliminating the chance of cross wiring.
Wired thermostats can be combined with wireless thermostats within the same system, if required.
Wired Room Thermostat should be mounted in a dry, indoor location, approximately 1.2m above the floor in an area with good air circulation. Avoid places with draughts, dead air spots and radiant heat from the sun or appliances.
Only one thermostat can be enrolled to each Control Centre's channel however a thermostat can be enrolled to multiple channels or other receivers without restriction, meaning one thermostat can control multiple UFH zones.
24V Bus Thermostats require 2 Core UTP Cable in lengths not exceeding 200m.
Floor temperature detection (optional) - the Hep2O Thermostat is equipped with an input terminal for temperature sensor connection. This is especially suitable for UFH control - by placing the sensor directly into the floor the heating regulation can be performed with higher precision (Remote Sensor Probe , purchased separately).
Warning: The UFH Wired Thermostat should not be installed in Wet Rooms (e.g. Bathrooms). When controlling Wet Rooms, the Thermostat should be located in a suitable location outside of the Wet Room, with the Remote Sensor Probe installed inside the Wet Room.